|Alarms||Individually enabled/disabled assigned a delay, assigned a priority, assigned to the summary alarm relay|
|Alarm Relay||Form C, dry contact|
|Mounting||Wall, shelf, floor, EIA 19-inch and 23-inch rack (front or rear)|
|Communication||Ethernet; 10/100BASE-TX; auto crossover, auto MDI-X; RJ45|
connector; support for TCP/IP, NTP, and SNMP Traps; internal
web server; ability to be used for networked comm or direct
comm (direct connection to a laptop)
|AC Input||Voltage Range, Rated: 100 – 240 VAC|
Voltage Range, Operating:
90 – 264 VAC
< 100 VAC: Reduced Power
Frequency, Rated: 50 – 200 Hz
Frequency, Operating: 45 – 205 Hz
> 91%, 120 Vac, full load;
> 93%, 240 Vac, full load;
> 0.98, 120 Vac, full load;
> 0.96, 240 Vac, full load
Protection: Current limit, surge, transient, under voltage, over voltage
|DC Output||Voltage Range:|
12 VDC: 1 – 20 VDC
24 VDC: 10 – 40 VDC
Power, Maximum, per iPM:
12 VDC: 400 W
24 VDC: 400 W
Current, Maximum, per iPM:
12 VDC: 20 A
24 VDC: 10 A
Current, Rated, per iPM:
12 VDC: 20 A
24 VDC: 10 A
Protection: Current limit, short circuit, reverse polarity, surge, transient
|Operating Environment||12, 24VDC: -40 – 70 °C (-40 – 158 °F)|
Storage Temperature: -55 – 85 °C (-67 – 185 °F)
Humidity Range: 0 – 95%, non-condensing
What are the mounting options for the charger?
The BC-2200 Charger can be mounted to the wall, on the floor, on a shelf, or on an EIA 19-inch or 23-inch rack (front or rear).
What kind of batteries are compatible to charge with the BC-2200?
The BC-2200 can charge batteries of a wide variety of types. These include Vented Lead-Acid (VLA), Valve Regulated Lead-Acid (VRLA), and Nickel-Cadmium (Ni-Cd).
What operating conditions should the charger be kept in?
The operating temperature range of the unit is -40 – 158ºF (-40 – 70ºC), and the operating humidity range is 0-95% relative humidity.
What method of cooling does the charger employ?
The BC-2200 was designed to stay cool by venting air using natural convection, which avoids potential electrical and safety issues which often arise when fans are used.
Can an iPM be replaced (hot swapped) while the charger is on?
Yes, the charger never needs to be powered down to replace an iPM.
Which components of the BC-2200 are microprocessor based?
All iPMs have microprocessors that interpret instructions from the UIM and then maintain those instructions as to how to care for the batteries. The UIM also has its own microprocessor for receiving and communicating instructions, as well as alarms. Since they all have their own processors that is what allows multiple failures in one chassis (including the UIM) and the charger will continue to provide DC voltage and current.
Is it possible to load share between multiple chargers?
The BC-2200 chargers will load share independently, no need for any special cables or added options. As one charger reaches capacity, another will ramp up quickly to support the incoming load. The BC-2200 chargers are highly filtered to operate as a DC power supply too, so they react extremely fast to load changes to support the load.