The Eagle Eye GFL-1000 Ground Fault Locator is an essential instrument to identify faulty grounding where electrical cables have breakage and loss to the ground. The unit identifies the inadvertent ground by injecting a low frequency signal on the faulted polarity. By following the signal using the current clamps and the portable receiver, the physical location of the ground fault can be found. Measurement of online DC systems is possible as the output current of the GFL-1000 is very low but the output voltage can be up to 1000V.
Compliance with NERC PRC005-6 requires that the battery and DC power system be inspected for inadvertent grounds every four months. If a ground fault exists the GFL-1000 is the tool by which that fault can be located without the need to de-energize the live circuit.
Patented technology, pinpoint current leakage fault with grounding resistance lower than 1MΩ
Ground fault testing for both offline and online DC systems
Waveform analysis will analyze the interference signal in the circuit
Wide output voltage range allows the GFL-1000 to meet the needs of your electronic equipment
Why should you measure battery ground faults? Battery ground faults are often times difficult to locate and create costly and catastrophic consequences if they remain undetected. The entire battery system will be compromised and subject itself to overheating, thermal runaway, and reduced battery capacity while creating a hazardous work environment.
Can the GFL-1000 test AC Systems? No, the GFL-1000 Ground Fault Locator will only test DC systems.
How does the GFL-1000 detect a fault? The ground fault detector works by injecting an AC signal into the bus system with respect to ground using the signal generator. The signal path is then traced using current clamps connected to the signal receiver. The direction of current flow is indicated on the receiver display, enabling the clamps to be moved to another branch or section of wiring. The measurement is repeated, the clamps moved again until the faulty part of the circuit is located.
What are some typical kinds of faults the GFL-1000 can test for? A typical supply to be tested will consist of a main bus connection with many branches to different loads or systems. Typical faults you may encounter are:
Fault from the positive bus to ground.
Fault from part of a load to ground.
Fault between bus bars (partial short circuit).
Fault from a branch to ground.
Fault from bus to a separate circuit (‘Wire Mix’ connection).
Leakage capacitance (This is not a fault, but leakage capacitance may be distributed around the system and will influence measurement).
In all cases, the actual impedance (resistance) of the fault may be very high, very low due to a short circuit, or anywhere in between.
How is the GFL-1000 powered? Both the signal generator and signal receiver use rechargeable batteries that can be charged using power supplies (110/220 VAC, 50/60 Hz) which are included in the GFL-1000 package. The state of charge for each unit is indicated by the icon in the top right hand corner of the unit’s display. Both units may be charged while switched off. When the units are fully charged an indicator on the power supply changes from red to green.
How long do the rechargeable batteries last on a full charge? The batteries will last for approximately 4 hours in normal use.
If you would like product specific training, please contact Eagle Eye directly. We offer complimentary training over the phone. Quotes can be provided for on site product-training. For more information call 1-877-805-3377 or email us at firstname.lastname@example.org. We provide timely support for all inquiries.
EEU Training Courses
Eagle Eye University (EEU) provides scheduled courses tailored to specific aspects of the critical power industry. All courses are also available at your location. The following courses are applicable to GFL-1000 Ground Fault Locator.